Comparison of Known PD Signals with the Developed and Commercial HFCT Sensors
Increasing need of cost effective identical sensors for partial discharge (PD) location prompted us to take up this research study. Four high-frequency current transformers (HFCT) were assembled and its performances with a used commercial sensor were compared with the known type of PD signals. In this paper, the responses due to surface, oil corona and air corona are analyzed. PD occurrence in 20 ms period and the shape of single PD with more sampled data points are characterized using seven techniques. The study indicates that HFCT with biflar winding is more sensitive in identifying different types of known PD. The number of turns and gauge of the used wire in HFCT play a role in increasing the sensitivity of PD detection.
Impact and interest:
Citation counts are sourced monthly from and citation databases.
These databases contain citations from different subsets of available publications and different time periods and thus the citation count from each is usually different. Some works are not in either database and no count is displayed. Scopus includes citations from articles published in 1996 onwards, and Web of Science® generally from 1980 onwards.
Citations counts from theindexing service can be viewed at the linked Google Scholar™ search.
Full-text downloads displays the total number of times this work’s files (e.g., a PDF) have been downloaded from QUT ePrints as well as the number of downloads in the previous 365 days. The count includes downloads for all files if a work has more than one.
|Item Type:||Journal Article|
|Divisions:||Past > QUT Faculties & Divisions > Faculty of Built Environment and Engineering|
|Copyright Owner:||Copyright 2007 IEEE|
|Copyright Statement:||Personal use of this material is permitted. However, permission to reprint/republish this material for advertising or promotional purposes or for creating new collective works for resale or redistribution to servers or lists, or to reuse any copyrighted component of this work in other works must be obtained from the IEEE.|
|Deposited On:||14 Nov 2007 00:00|
|Last Modified:||29 Feb 2012 13:31|
Repository Staff Only: item control page