Use of IEEE 1588-2008 for a sampled value process bus in transmission substations
Ingram, David M.E., Campbell, Duncan, & Schaub, Pascal (2011) Use of IEEE 1588-2008 for a sampled value process bus in transmission substations. In 2011 IEEE International Instrumentation and Measurement Technology Conference (I2MTC 2011) Proceedings, IEEE, Binjiang, Hangzhou, China, pp. 871-876.
IEC Technical Committee 57 (TC57) published a series of standards and technical reports for “Communication networks and systems for power utility automation” as the IEC 61850 series. Sampled value (SV) process buses allow for the removal of potentially lethal voltages and damaging currents inside substation control rooms and marshalling kiosks, reduce the amount of cabling required in substations, and facilitate the adoption of non-conventional instrument transformers. IEC 61850-9-2 provides an inter-operable solution to support multi-vendor process bus solutions.
A time synchronisation system is required for a SV process bus, however the details are not defined in IEC 61850-9-2. IEEE Std 1588-2008, Precision Time Protocol version 2 (PTPv2), provides the greatest accuracy of network based time transfer systems, with timing errors of less than 100 ns achievable. PTPv2 is proposed by the IEC Smart Grid Strategy Group to synchronise IEC 61850 based substation automation systems. IEC 61850-9-2, PTPv2 and Ethernet are three complementary protocols that together define the future of sampled value digital process connections in substations.
The suitability of PTPv2 for use with SV is evaluated, with preliminary results indicating that steady state performance is acceptable (jitter < 300 ns), and that extremely stable grandmaster oscillators are required to ensure SV timing requirements are met when recovering from loss of external synchronisation (such as GPS).
Impact and interest:
Citation counts are sourced monthly from and citation databases.
These databases contain citations from different subsets of available publications and different time periods and thus the citation count from each is usually different. Some works are not in either database and no count is displayed. Scopus includes citations from articles published in 1996 onwards, and Web of Science® generally from 1980 onwards.
Citations counts from theindexing service can be viewed at the linked Google Scholar™ search.
Full-text downloads displays the total number of times this work’s files (e.g., a PDF) have been downloaded from QUT ePrints as well as the number of downloads in the previous 365 days. The count includes downloads for all files if a work has more than one.
|Item Type:||Conference Paper|
|Additional Information:||This paper was peer reviewed as an extended abstract (4 page paper) by two external reviewers.|
|Keywords:||ethernet networks, IEC 61850, IEEE 1588, performance evaluation, power system simulation, power transmission, protective relaying, smart grids, time measurement|
|Subjects:||Australian and New Zealand Standard Research Classification > ENGINEERING (090000) > ELECTRICAL AND ELECTRONIC ENGINEERING (090600) > Control Systems Robotics and Automation (090602)
Australian and New Zealand Standard Research Classification > ENGINEERING (090000) > ELECTRICAL AND ELECTRONIC ENGINEERING (090600) > Industrial Electronics (090603)
Australian and New Zealand Standard Research Classification > ENGINEERING (090000) > ELECTRICAL AND ELECTRONIC ENGINEERING (090600) > Power and Energy Systems Engineering (excl. Renewable Power) (090607)
|Divisions:||Past > QUT Faculties & Divisions > Faculty of Built Environment and Engineering
Past > Schools > School of Engineering Systems
|Copyright Owner:||Copyright 2011 IEEE|
|Copyright Statement:||Personal use of this material is permitted. However, permission to reprint/republish this material for advertising or promotional purposes or for creating new collective works for resale or redistribution to servers or lists, or to reuse any copyrighted component of this work in other works must be obtained from the IEEE.|
|Deposited On:||25 Feb 2011 03:05|
|Last Modified:||15 Nov 2011 21:59|
Repository Staff Only: item control page