Performance analysis of PTP components for IEC 61850 process bus applications
Ingram, David M.E., Schaub, Pascal, Campbell, Duncan A., & Taylor, Richard R. (2013) Performance analysis of PTP components for IEC 61850 process bus applications. IEEE Transactions on Instrumentation and Measurement, 62(4), pp. 710-719.
New substation automation applications, such as sampled value process buses and synchrophasors, require sampling accuracy of 1 µs or better. The Precision Time Protocol (PTP), IEEE Std 1588, achieves this level of performance and integrates well into Ethernet based substation networks. This paper takes a systematic approach to the performance evaluation of commercially available PTP devices (grandmaster, slave, transparent and boundary clocks) from a variety of manufacturers. The ``error budget'' is set by the performance requirements of each application. The ``expenditure'' of this error budget by each component is valuable information for a system designer. The component information is used to design a synchronization system that meets the overall functional requirements. The quantitative performance data presented shows that this testing is effective and informative. Results from testing PTP performance in the presence of sampled value process bus traffic demonstrate the benefit of a ``bottom up'' component testing approach combined with ``top down'' system verification tests. A test method that uses a precision Ethernet capture card, rather than dedicated PTP test sets, to determine the Correction Field Error of transparent clocks is presented. This test is particularly relevant for highly loaded Ethernet networks with stringent timing requirements. The methods presented can be used for development purposes by manufacturers, or by system integrators for acceptance testing. A sampled value process bus was used as the test application for the systematic approach described in this paper. The test approach was applied, components were selected, and the system performance verified to meet the application's requirements. Systematic testing, as presented in this paper, is applicable to a range of industries that use, rather than develop, PTP for time transfer.
Citation countsare sourced monthly fromand citation databases.
These databases contain citations from different subsets of available publications and different time periods and thus the citation count from each is usually different. Some works are not in either database and no count is displayed. Scopus includes citations from articles published in 1996 onwards, and Web of Science® generally from 1980 onwards.
Citations counts from theindexing service can be viewed at the linked Google Scholar™ search.
Full-text downloadsdisplays the total number of times this work’s files (e.g., a PDF) have been downloaded from QUT ePrints as well as the number of downloads in the previous 365 days. The count includes downloads for all files if a work has more than one.
|Item Type:||Journal Article|
|Keywords:||Ethernet networks, IEC 61850, IEEE 1588, performance evaluation, power transmission, protective relaying, Precision Time Protocol, smart grids, time measurement|
|Subjects:||Australian and New Zealand Standard Research Classification > ENGINEERING (090000) > ELECTRICAL AND ELECTRONIC ENGINEERING (090600) > Power and Energy Systems Engineering (excl. Renewable Power) (090607)|
Australian and New Zealand Standard Research Classification > ENGINEERING (090000) > ELECTRICAL AND ELECTRONIC ENGINEERING (090600) > Electrical and Electronic Engineering not elsewhere classified (090699)
Australian and New Zealand Standard Research Classification > TECHNOLOGY (100000) > COMMUNICATIONS TECHNOLOGIES (100500) > Computer Communications Networks (100503)
|Divisions:||Current > Schools > School of Electrical Engineering & Computer Science|
Current > QUT Faculties and Divisions > Science & Engineering Faculty
|Copyright Owner:||Copyright IEEE 2012|
|Copyright Statement:||Personal use of this material is permitted. However, permission to reprint/republish this material for advertising or promotional purposes or for creating new collective works for resale or redistribution to servers or lists, or to reuse any copyrighted component of this work in other works must be obtained from the IEEE.|
|Deposited On:||13 Sep 2012 08:16|
|Last Modified:||23 Apr 2013 20:09|
Repository Staff Only: item control page