Performance analysis of IEC 61850 sampled value process bus networks
Ingram, David M.E., Schaub, Pascal , Taylor, Richard R., & Campbell, Duncan A. (2012) Performance analysis of IEC 61850 sampled value process bus networks. IEEE Transactions on Industrial Informatics, 9(3), pp. 1445-1454.
Process bus networks are the next stage in the evolution of substation design, bringing digital technology to the high voltage switchyard. Benefits of process buses include facilitating the use of Non-Conventional Instrument Transformers, improved disturbance recording and phasor measurement and the removal of costly, and potentially hazardous, copper cabling from substation switchyards and control rooms. This paper examines the role a process bus plays in an IEC 61850 based Substation Automation System. Measurements taken from a process bus substation are used to develop an understanding of the network characteristics of "whole of substation" process buses. The concept of "coherent transmission" is presented and the impact of this on Ethernet switches is examined. Experiments based on substation observations are used to investigate in detail the behavior of Ethernet switches with sampled value traffic. Test methods that can be used to assess the adequacy of a network are proposed, and examples of the application and interpretation of these tests are provided. Once sampled value frames are queued by an Ethernet switch the additional delay incurred by subsequent switches is minimal, and this allows their use in switchyards to further reduce communications cabling, without significantly impacting operation. The performance and reliability of a process bus network operating with close to the theoretical maximum number of digital sampling units (merging units or electronic instrument transformers) was investigated with networking equipment from several vendors, and has been demonstrated to be acceptable.
Impact and interest:
Citation countsare sourced monthly fromand citation databases.
These databases contain citations from different subsets of available publications and different time periods and thus the citation count from each is usually different. Some works are not in either database and no count is displayed. Scopus includes citations from articles published in 1996 onwards, and Web of Science® generally from 1980 onwards.
Citations counts from theindexing service can be viewed at the linked Google Scholar™ search.
Full-text downloadsdisplays the total number of times this work’s files (e.g., a PDF) have been downloaded from QUT ePrints as well as the number of downloads in the previous 365 days. The count includes downloads for all files if a work has more than one.
|Item Type:||Journal Article|
|Keywords:||Ethernet networks, IEC 61850, performance evaluation, process bus, power transmission, protective relaying, smart grids|
|Subjects:||Australian and New Zealand Standard Research Classification > INFORMATION AND COMPUTING SCIENCES (080000) > DISTRIBUTED COMPUTING (080500) > Networking and Communications (080503)|
Australian and New Zealand Standard Research Classification > ENGINEERING (090000) > ELECTRICAL AND ELECTRONIC ENGINEERING (090600) > Power and Energy Systems Engineering (excl. Renewable Power) (090607)
Australian and New Zealand Standard Research Classification > TECHNOLOGY (100000) > COMMUNICATIONS TECHNOLOGIES (100500) > Computer Communications Networks (100503)
|Divisions:||Current > Schools > School of Electrical Engineering & Computer Science|
Current > QUT Faculties and Divisions > Science & Engineering Faculty
|Copyright Owner:||Copyright 2012 IEEE|
|Copyright Statement:||© 2012 IEEE. Personal use of this material is permitted. Permission from IEEE must be obtained for all other uses, in any current or future media, including reprinting/republishing this material for advertising or promotional purposes, creating new collective works, for resale or redistribution to servers or lists, or reuse of any copyrighted component of this work in other works.|
|Deposited On:||19 Nov 2012 12:31|
|Last Modified:||22 Aug 2013 01:47|
Repository Staff Only: item control page